Air compressor: Installation standards and requirements of air compressor
Air compressor: 1, air compressor installation environment layout requirements
To meet the requirements of development, the equipment room should have room for expansion on the general diagram.
An air compressor draws air directly from the atmosphere. To prevent unit wear, corrosion, and explosion, keep a certain distance between the equipment room and places that emit explosive, corrosive, toxic gas, and dust. The heat dissipation capacity is large, especially in summer, the temperature inside the machine is very high, so the direction of the machine room should make the machine room well ventilated, and minimize sunlight exposure.
Although the compressor has a cabinet, but it is forbidden to rain, so the compressor should not be installed in the open air. The compressor room shall be a separate building.
The compressor room must be equipped with fixed carbon dioxide fire extinguishing equipment, and its manual switch must be set outside the danger zone. And can be touched at any time. Fire extinguishing equipment Carbon dioxide fire extinguisher or dry powder fire extinguisher should be placed near the protected target, but should be placed outside the danger area.
2. Installation requirements of air compressor machine room
The floor is smooth cement floor, the inner surface of the wall should be white, the compressor base should be placed on the cement floor, and the plane height is not greater than 0.5/1000 (mm). About 200mm away from the unit is provided with a groove, so that when the unit stops for oil change, maintenance or cleaning the ground, oil and water can flow out of the groove. The size of the groove is determined by the user.
The compressor unit is placed on the ground, and the bottom of the box should be in good contact with the ground to prevent vibration and increase noise.
For qualified users, you can paste sound-absorbing boards on the walls of the machine room to further reduce noise, but it is not suitable to decorate the walls with hard surface materials such as ceramic tiles.
The air-cooled compressor is greatly affected by the ambient temperature. Therefore, the equipment room must be well-ventilated and dry. The heat exchange air can be extracted from the outdoor air duct or exhaust fan to control the compressor's ambient temperature between -5°C and 40°C. The temperature in the equipment room should be above 0 ° C.
The equipment room has less dust and fresh air, free of harmful gases and corrosive media such as sulfite. According to the nature of the products processed by your company, the air inlet should be equipped with a filter device. Window circulation effective area should be more than 3 square meters
Shijiazhuang Compus Compressor Co., Ltd. main products are oil-free air compressor, high pressure air compressor, screw air compressor, air compressor, drilling air compressor, oil-free mobile machine, high pressure mobile machine, drilling machine, two-stage compression screw machine, permanent magnet variable frequency screw machine, mine explosion-proof screw machine, air floating centrifugal blower and so on. At present, the company has established 30 customer service networks and more than 100 dealers in the country, to provide customers with pre-sales technical consultation, machine sales, on-site maintenance, parts supply 4S services. The enterprise's good faith service is well received by users. Adhering to the core concept of "quality first, customer satisfaction", we always adhere to provide customers with high-quality products and technical services, we firmly believe that Compus will become your more reliable partner, and are willing to work with you to achieve glory!